UPDATE 2022-02-16: Venus OS v2.81 till v2.84 has been released. Details in the change log on https://professional.victronenergy.com; those versions mostly contain fixes relating to v2.80 – no new features. It is recommended to update to v2.84.
CORRECTION 2022-02-16: The Bluetooth Radio in the Cerbo GX is not reliable enough to work with the Ruuvi sensors. Therefore, when installing Ruuvi sensors, we recommend to install a Bluetooth USB adapter. More information in below text, which has been updated.
Today we are releasing Venus OS v2.80, a major new release full of new features and improvements.
In this blog post I’ll go through the highlights. A link to the full changelog can be found at the end of this post, as well as instructions on how to update.
For those not familiar with Venus OS: Venus OS is the software running on our Cerbo GX monitoring system, as well as its predecessors the Color Control GX, Venus GX and more. Also, it is in the GX versions of our MultiPlus-II and EasySolar-II inverter/chargers.
The main new features are:
- Support for the wireless Ruuvi temperature sensors, which measure humidity and air pressure as well.
- Controlling a relay on temperature
- Monitoring of AC as well as DC loads
- Improved support for VRM overview details
- Complete support for Inverter RS, and add preliminary support for the new Multi RS.
There is much more still, the official changelog entry consists of multiple pages, as well as this blog post – lets start with the first new feature.
#1 – Wireless and battery powered temp sensors: the Ruuvi
Something quite new, and far more popular then I anticipated to be honest: the support for the Ruuvi temperature sensors. Being powered by a small coin cell in the sensor, as well as wireless, they are super simple to install. And as such perfect to remotely keep an eye on your yacht or cabin in the winter. Or fridge or freezer temperatures, and so forth.
I have installed and am using some myself as well, and they are great. Less stress about pipes freezing up, as well as mould growing: it also reports relative humidity.
Here is a picture showing the sensor, and the reported data:
Here is how the data looks on the VRM Portal:
A few notes:
- Victron is not stocking the Ruuvi sensors. They are available for purchase directly from ruuvi.com.
- To read data from the Ruuvi sensor, a Bluetooth USB adapter is required. For CCGX, Venus GX, and also for the Cerbo GX. A list of suitable and tested Bluetooth USB adapters is available in this post on Victron Community.
- Per v2.82, multiple Bluetooth USB adapters can be installed and will all be used to read data from the Ruuvis. This is nice, as it allows expanding the range by using a USB extension cable.
See the documentation for more details about this feature.
#2 – Controlling a relay on temperature
The relays on the GX device can now be controlled by temperature. For example to switch a fan, or heating pad. Here are two screenshots showing the configuration:
In above example, the second relay will switch when the temperature in the engine bay rises above 45 degrees, starting the fan. And it will switch off once the temperature drops below 40 degrees C.
Both the first and the second relay can be configured to be controlled by temperature. And two sets of conditions can be configured, also for the same relay.
#3 – DC energy monitoring
The next improvement is the ability to use the SmartShunt or BMV-712 for DC metering.
Here are a few examples of what to use it for:
- Monitor the output of an alternator.
- Accurately measure and monitor the DC system on a boat, RV or coach.
- Independently measure the DC systems on the Port hull, and Starboard hull of a catamaran.
- Monitor a specific load or group of loads, such as a fridge.
When the Shunt is configured as “DC Energy Meter” (in VictronConnect), and the GX is enabled with “has DC system”, the GX does more than just recording and visualisation:
- It uses that measurement for display in the DC system power box on the overview, rather than the calculated, and as such often inaccurate, difference between Shunt and connected inverters and chargers.
- When using DVCC, the GX device will automatically increase the chargers to compensate for that load. An example: maximum charge current configured at 50 Amps, and DC system shunt reports a draw of 25 Amps. Then the chargers are set to charge with 50 + 25 = 75 Amps. A welcome improvement for applications with heavy DC loads, such as yachts and coaches.
Using the DC metering for anything else, not DC system, has no effect on the system behaviour. In that case it’s just measuring and making the data available to monitor.
To use these features, use VictronConnect to configure the SmartShunt or BMV-712 to be a meter, in the Misc Settings menus.
This screenshot shows an example system, a catamaran, having five shunts installed: one at the battery for state of charge, and one at each alternator, and one for the DC circuit in each of the hulls:
#4 – AC energy metering
AC meters, such as the supported Carlo Gavazzi meters, can now be used to measure a load, or a circuit having multiple loads. Once installed, configured to a new “role”: AC Load monitor. This is done in the GX menu where you also choose between Grid, PV Inverter and Generator. With AC Load monitor selected, the load will be shown in the Device list.
Support for this new feature will also be coming to VRM shortly.
We also increased the maximum possible power value for starting a generator, it was previously 100kW, and now has been increased to 1MW.
#5 – VRM Dashboard improvements
More information has been added to generator view (running/not running, last run, why it’s running, and more) on the VRM Portal Dashboard, when enabling the Detailed view.
More detailed information about AC input (grid/shore) as well as AC Loads, including frequency has been added.
#6 – MultiPlus-II 2x120V – 2nd leg power and amps
Support has been added to show output current & power on the second leg of the MultiPlus-II 2x120V. That model of inverter/charger was launched last year and aimed at the North American market – where docks and camping grounds sometimes offer a single phase supply, and sometimes a dual phase.
These screenshots shows the data, in the Device list (left), Overview (right) as well as on the VRM Portal (bottom).
#7 Marine MFD App improvements
We have added a lock button that helps prevent accidental button presses like “Start generator” or “Multi Off”. There are several other MFD improvements to fix bugs, compatibility and additional languages – see the release notes for more specifics.
#8 Inverter RS: DVCC and more – all done
This is the first version of Venus OS that is compatible with the brand new Multi RS, which is now becoming available for order with very limited stock – however many significant limitations still apply. Complete support for Multi RS is expected to be completed in February or March 2022.
#9 Connectivity improvements
- Improved WiFi recovery from ‘Failure’ status.
- Improved ET340 in combination with Zigbee link
- Fixed Bluetooth pincodes starting with a 0 (zero)
- Improved Bluetooth connections (keep-alive functionality, and “busy” indication in VictronConnect)
- Added confirmation before forgetting/disconnecting from a WiFi network, as well as before disabling the WiFi Access Point; to prevent accidental lock out, especially when remote.
- CPU load optimisations – especially when connected to AC PV inverters
#10 ESS change for multi-phase systems configured to “Total of all phases” mode
For split- and three-phase ESS systems, with their mode configured to “Total of all phases”, the behaviour has been optimised to be symmetrical. All phases are now adjusted to convert the same amount of power from, as well as to, DC.
In the past, this option primarily avoided passing power through the DC-bus to avoid inefficiency, but didn’t take full advantage of the billing arrangement to use all the available power when there is a shortfall on another phase. Now it divides the work equally across the phases, thereby making the full inverter capacity available, and with no impact on billing.
This change will mainly benefit systems having inverters that are smaller than the maximum per phase load.
#11 – DVCC – Pylontech, BMZ, Lynx Smart BMS
There are various small fixes and improvements, these are the highlights:
- DVCC is now force enabled for Pylontech and BMZ batteries, as well as Victron Lithium batteries installed using the Lynx Smart BMS. By force enabling this setting, fewer mistakes can be made in the configuration, and this change builds on the experience of doing the same with BYD, BSL Batteries, Freedomwon, Blue Nova and Discover AES in earlier releases.
- Automatically switch to charging when a grid connection is available and a managed battery requests charge. Currently only Pylontech and some BYD batteries support a charge request indication.
More details are in the change log
#12 – Still more changes and conclusion
Besides the items above, there are many more changes. All rather minor and related to certain specific situations or systems. To read them, find the full change log by logging into Victron Professional and selecting ‘Firmware’ -> ‘Venus OS’ -> ‘firmware changelog’.
Information about how to install the firmware is in the manual of your GX Device. Quick links to the relevant pages: Cerbo GX, Color Control GX and for the Venus GX.
That is it for now, sincerely yours,
Victron Energy BV